Regenerative Thermal Oxidizers
Rule of Thumb Calculations
How much fuel does an RTO with 95% Heat Recovery consume when operating at 1500°F?
The enthalpy of air at 1500°F is 28.24 BTU/Ft3.
Disregarding the incoming temperature, the amount of heat required will be:
0.05 x 28.24 = 1.412 BTU/Ft3
Assuming a heat loss of 10%, this becomes:
1.412 x 1.1 = 1.5532 BTU/Ft3 ~ 1.6 MMBTU/H
Now insert the flow rate in SCFM (ex. 10,000 SCFM):
10,000 x 1.6 x 60 = 0.96 MMBTU/H (< 1.0 MMBTU/H)
If process emits 60 lbs/hr of VOC (alcohol & acetate) with a BTU content of 13,000 BTU/lb:
60 x 13,000 = 0.78 MMBTU/H
The RTO burner will be:
0.96 – 0.78 = 0.18 MMBTU/H or 180,000 BTU/H or 180 ft3 /H of Natural Gas
If heat value of the VOC is greater than shown, the burner will consume less fuel.
For more Ship & Shore environmental engineering insights and technical information,
please contact firstname.lastname@example.org
Copyright © 2019 Ship and Shore Environmental, Inc. All rights reserved.